Attention and requirement during probe installation.
Please install probe in the axis of tank as manhole, and keep the distance between probe, delivery pipe and suction pipe must be
more than 1 meter. Otherwise, the oil flow will influence on the probe performance, even bend and damage the probe.
During the installation, it is important to adjust outlet direction of delivery pipe to opposite to the probe. Riser pipe must be welded
vertical (vertical for horizontal not for manhole cover), insert into manhole cover but not more than 100mm. Internal wall of riser
pipe must be smooth and no welding slag. Correct installation please sees Fig 1 as below.